Tips on Home Generators
Anyone considering the purchase of a standby generator should be aware of a number of factors before purchasing and installing. For technical requirements on permanent generators, see Customer's Standby Generation Installations from OPPD's Meter Specifications Manual.
- Standby generators are designed for home and farm use in a variety of models and sizes.
- Sizes of standby generators range from an output of 1 kilowatt (kw) to over 100 kw.
- Portable gasoline engine generators are designed to provide a reliable source of portable power for a wide variety of applications.
- Engines usually run on gas or diesel, but models are also available for propane or natural gas.
Sizing of Home Generators
- Manufacturers rate each standby generator on how much power (kw to kva) it is capable of supplying. That rating is noted on the generator's nameplate.
- A generator can be purchased with the capability of supplying an entire residence, or a smaller generator can be purchased to supply only a portion of a home's electrical load.
- The total electric load on your generator must not exceed the manufacturer's rating.
- If the generator will supply only a portion of the home's electrical load, a list should made of the electrical equipment to be powered during a utility outage (e.g., appliances, lamps, home furnace blower motor, etc.). Compare the total wattage of the equipment to the total wattage output rating of the generator (if an item is rated in amps, simply multiply the amps by the voltage to determine the wattage). For example, to power ten 100-watt light bulbs, the generator should be rated at least 1,000 watts.
- The generator should be capable of starting the largest motor that is supplied by the generator under emergency conditions. If a group of motors is to be started simultaneously under emergency conditions, the generator must be capable of supplying the required starting current for each motor.
- If it is decided the generator should have the capacity to supply an entire residence, the KW rating of the standby generator should be greater than the maximum full load of the residence.
Installation of a Standby Generator (Portable)
- Portable generators are designed for connection only to smaller selected appliances or lamps. They should never be connected directly to a building's wiring system.
- Carefully read all instructions included with the generator before operating it. Be sure that the total electric load on your generator does not exceed the manufacturer's rating.
- Portable generators should be kept outside during use to ensure the exhaust will vent safely. (Use of a generator in an enclosed area may cause a buildup of carbon monoxide or other harmful exhaust gases.)
- Always wait five minutes or more for the generator to cool down prior to refueling.
- Keep extension cords out of the way or protected so they don't present a tripping hazard.
- Never run electrical cords under rugs or carpets, where damage to a cord may go unnoticed or heat might build up. Make sure cords are properly sized to carry the electric load, as overloaded cords can overheat and cause fires.
Installation of Standby Generators (Permanent)
- Customer's Standby Generation Installations (From OPPD's Meter Specifications Manual.)
- Permanent Installation of a larger generator set may require a concrete foundation support the engine and generator.
- To allow a home generator set to provide power through the house electrical distribution system, a transfer switch must be installed. The transfer switch (also called a throw-over switch) allows the electrical load to be connected to either the generator supply or utility supply, but prevents simultaneous connection. NOTE: Severe consequences will result if a transfer switch is not used when connecting a standby generator. Among other things, simultaneous connection can cause the generator to backfeed onto OPPD's distribution system, resulting in an unsafe condition that could damage equipment or electrocute line crews working on de-energized lines.
- Transfer switches are available in either manual or automatic operation.
- Transfer switches should always be rated to carry the larger of the maximum full load of the residence or the full output of the standby generator.
General Safety Rules for the Use of Standby Generators
- All wiring and equipment must comply with local, state and federal laws or codes, and rules and regulations of OPPD.
- All wiring and equipment must have approval of the local inspection authority.
- The standby generator must be rated at 60-hertz alternating current, and the voltage rating must be the same as the service voltage supplied by OPPD.
- Automatic transfer switch systems must be approved by OPPD.
- The general arrangement of the wiring and equipment must prevent any accidental connection between the usual supply and the alternate supply.
- Only a qualified professional, such as a licensed electrical contractor, should install a permanent standby generator.
- Use your standby generator correctly. Carefully read and follow the manufacturer's instructions.
Any questions regarding transfer switches should be referred to OPPD's Energy Advisor at 402-636-3850 or 1-800-648-2658. For service voltages over 600 volts, call the Electric Service Designer in your area.